The manufacturer of the buried anti floating integrated box pump station is directly selling. If you want to know more about the situation of the buried anti floating integrated box pump station, please consult 18095174046 via wechat or telephone
Classification of buried anti floating integrated box pumping station:
1. Underground box pump integrated automatic constant pressure fire water supply equipment
2. Underground BDF assembled box pump integrated fire booster equipment
3. Anti floating buried box type integrated fire water supply pump station
4. Integrated fire fighting equipment of dry-type motor and buried box pump
5. Integrated pump station of living box pump
Introduction to buried anti floating integrated box pump station:
1. The underground box pump integrated fire pump station is mainly composed of fire pool, fire pump room, fire-fighting booster water supply equipment system and sewage system.
2. The structural form of fire pump station is: all steel structure
3. The installation form of fire pump station is: bolt assembly and welding
4. The location of fire pump station is: ground or underground buried anti floating tank pump integrated material: hot galvanized or stainless steel or composite steel plate or galvanized steel plate and 304 stainless steel composite plate
5. 304 stainless steel or clad stainless steel pump house
6. Internal structure and material of fire pump station pool: full scaffold structure or portal steel frame structure; hot-dip galvanized steel pipe;
7. The pump station is made of I-shaped steel or reinforced steel structure
8. Bearing capacity of pump station: 100-450kn / m2
9. Service life of fire pump station: more than 30 years
10. Foundation of fire pump station: raft foundation is adopted
11. The water tank of fire pump station is impermeable and leakproof: EPDM rubber sealing strip is used
12. The diameter of the vent pipe of the fire pump station shall be DN 100 and led to the sump
13. The ventilation of the pump house of the fire pump station is: the use of 24h unpowered ventilator
14. The heating of the pump house of the fire pump station adopts the automatic constant temperature device when the temperature of the pump room is lower than 5 ℃
15. The fire resistance rating of fire pump station is grade II.
16. The plane size of the manhole in the pump house of the fire pump station is 2m × 2m
17. The material of corner stairs in pump house of fire pump station is hot-dip galvanized steel plate
18. A magnetic level gauge is installed in the pump house of the fire pump station to display the water level in the water tank.
19. The outlet pipe of the fire fighting system in the fire pump station adopts double outlet.
20. The control cabinet in the buried integrated box pump station has the functions of automatic start, manual start, remote control start, mechanical start, high and low water level alarm, automatic low frequency inspection and manual power frequency inspection, fault memory output, flow detection, remote monitoring and communication.
The fire protection level of the pump station is IP55
22. The inspection period of water pump in fire pump station is 7 days, and each pump inspection time is 2min
23. According to GB 50974-2014, the effective volume of the high-level fire water tank of the temporary high-pressure fire water supply system should meet the requirements of the initial fire-fighting water consumption.
24. The effective volume and minimum effective water level of high-level fire water tank shall meet the hydrostatic pressure at unfavorable points of water fire-fighting facilities.
25. The main parts of the pump shell and impeller of the stabilized pressure pump in the buried integrated box pump station should be made of stainless steel.