Yinchuan high quality stainless steel water tank
07-12 nine hundred and forty
Yinchuan high quality stainless steel water tank
1、 Yinchuan stainless steel water tank manufacturing standard: National Building Standard Design Atlas 12s101; stainless steel water tank body is assembled and welded by convex formwork, which can be flexibly assembled according to the site structure, different size requirements and different tonnage requirements, with less consumables, higher structural strength, no need of large hoisting equipment, and convenient transportation. 2、 Yinchuan water tank materials: SUS304 series, SUS316 series or SUS444 series
3、 Application scope of Yinchuan water tank:
1. Life stainless steel water tank is suitable for large hotels, offices, apartments, scientific research and teaching buildings, food processing, medical and health, electronic industry and other places with high water quality requirements.
2. Various industrial and civil building water supply, heating and ventilation, fire fighting system; food, beverage, wine making, water treatment industry; medicine, petroleum, chemical industry; flexible and reasonable plate shape design can be suitable for containers of various sizes combination.
4、 Features of Yinchuan water tank:
1. Excellent material selection: high quality food grade stainless steel SUS304 / 316 / 444 can greatly prolong the service life of the water tank, and can better prevent the secondary pollution of water quality.
2. Unique and reasonable structure: high strength stamping plate and stainless steel tie bars evenly distributed in the box make the box pressure uniform and reasonable.
3. Convenient and fast construction: the standard stamping plates of 1000X1000, 1000X500 and 500x500mm can be assembled and welded at will without hoisting equipment.
It not only reduces the thickness of the pressure bearing box, but also meets the requirements of the pressing process.
5、 Installation instructions of Yinchuan stainless steel water tank
1. Requirements for water tank foundation
The geometric dimension of concrete foundation shall be formulated according to relevant provisions of gb02s101.
The plane height difference of concrete foundation is less than 5mm;
Non standard water tank concrete foundation is designed by our company.
2. Installation, construction and acceptance of water tank
Professional welder site argon arc welding.
The construction site has standard power supply. There is no less than 500mm maintenance space around the water tank.
It is qualified if there is no corrosion and pollution in appearance inspection; if the box is filled with water for 2-3 h, there is no obvious deformation of the box and no leakage of the weld.
3. Use, repair and maintenance of water tank
When piping, do not apply excessive load to the inlet and outlet of piping.
Do not directly apply the weight of valve and large diameter pipe to the water tank nozzle, and set up pipe support if necessary.
Expansion flexible joint must be installed for expansion, contraction and vibration of welded pipe.
4. Water tank configuration and accessories
The supply scope of water tank of our company includes box, manhole with lock, ladder, short pipe and single flange.
The company can also provide supporting accessories according to the requirements of users, such as: floating ball valve, glass tube level gauge and various water tank disinfection equipment.
6、 "Stainless steel" or "stainless steel" channel beam can be used for inspection. The top corner of the stainless steel water tank is equipped with a ventilation air filtering device. The specification and quantity of the device are determined by the manufacturer according to the import size. Tie bars are used inside the stainless steel water tank. All nozzle flanges are 1.0MPa standard flange. Designers should refer to GB 17051-1997 sanitary code for secondary water supply facilities when arranging the water tank position. When the specification and technical parameters or orientation of the water tank are not suitable for the actual use, the designer of the stainless steel water tank shall propose and determine it according to the actual needs.
1. The stainless steel water tank has no leakage after 48 hours of full water test;
2. Whether there is water leakage at the pipe joints, valves and relevant accessories;
3. Observe whether the water supply system operates normally;
4. Check whether the water disinfection system works normally.
7、 Cleaning and maintenance of stainless steel water tank
1. Close the inlet valve and open the drain outlet valve to drain the water in the water tank;
2. Enter the water tank through the ladder;
3. Clean the periphery and bottom of water tank with clean mop or cloth. If the scale is serious at the bottom, it can be scrubbed with soft towel and detergent;
4. Open the water inlet valve and flush the wall and bottom of the barrel with proper amount of clean water, so that the dirt can be discharged from the drain outlet. If necessary, it can be repeated several times until it is satisfactory;
5. Close the drain valve, open the water inlet valve, and fill the water tank with water again.
Yinchuan water tank specifications can be formulated according to the specifications required by customers; Ningxia Jiquan water supply equipment Co., Ltd. welcome to discuss 180-95174046; we will serve you wholeheartedly!